for Xenia, OH
Ken - Xenia, OH
Great response from Aaron. Kept me informed of all issues along the way.
Upon arrival power was off to 2006 Goodman furnace, turned on and called for heat at thermostat and fault code 3 pressure switch, Tested system it's rated to close at .35 inwc and it's good, Tested inducer motor it's over amping, it is pulling 1.10 inwc enough to close switch, The circuit board is bad and needs replaced, also recommend replacing inducer motor due to it over amping, System not operational at departure.